The template implements support for Goboy 1M Gas Counters.

Communication protocol of the devices is based on ModBus but it implements only nonstandard functions.

Parameters, provided by this protocol, are all static, that is the representative attributes are provided by the template. For archiving parameters (7) there are provided hourly, daily and month archives.

The template works in two modes: initial and tracing. Where the initial mode means first reading all archives from hourly one and switching to the tracing mode after finish the reading, that is reading fresh archiving and current data.

Status of the template is shown in the "Error (err)" attribute with information about the mode and position of the read data of the archives.

Author: Roman Savochenko <roman@oscada.org>
Total complexity: 1.0 HD
Ordered by: BLUE STAR GROUP Ltd
Version: 1.0.0
License: GPLv2